- Volume 10 Issue 5
DOI QR Code
Optimal Reserve Allocation to Maximize Kinetic Energy in a Wind Power Plant
- Yoon, Gihwan ;
- Lee, Hyewon ;
- Lee, Jinsik ;
- Yoon, Gi-Gab ;
- Park, Jong Keun ;
- Kang, Yong Cheol
- Received : 2015.02.24
- Accepted : 2015.06.05
- Published : 2015.09.01
Modern wind generators (WGs) are forced or encouraged to participate in frequency control in the form of inertial and/or primary control to improve the frequency stability of power systems. To participate in primary control, WGs should perform deloaded operation that maintains reserve power using speed and/or pitch-angle control. This paper proposes an optimization formulation that allocates the required reserve to WGs to maximize the kinetic energy (KE) stored in a wind power plant (WPP). The proposed optimization formulation considers the rotor speed margin of each WG to the maximum speed limit, which is different from each other because of the wake effects in a WPP. As a result, the proposed formulation allows a WG with a lower rotor speed to retain more KE in the WPP. The performance of the proposed formulation was investigated in a 100-MW WPP consisting of 20 units of 5-MW permanent magnet synchronous generators using an EMTP-RV simulator. The results show that the proposed formulation retains the maximum amount of KE with the same reserve and successfully increases the frequency nadir in a power system by releasing the stored KE in a WPP in the case of a disturbance.
Deloaded operation;Frequency support;Kinetic energy;Primary control;Wake effect;Wind power plant
- Global Wind Energy Council, "Global wind report: annual market update 2013," Apr. 2014.
- The Ministry of Knowledge Economy, "The 6th basic plan of long term electricity supply and demand," Feb. 2013.
- O. Anaya-lara, N. Jenkins, J. Ekanayake, P. Cartwright, and M. Hughes, Wind Energy Generation Modeling and Control: John Wiley & Sons, Ltd, 2009.
- J. Ekanayake and N. Jenkins, “Comparison of the response of doubly fed and fixed-speed induction generator wind turbines to changes in network frequency,” IEEE Trans. Energy Convers., vol. 19, no. 4, pp. 800-802, Dec. 2004. https://doi.org/10.1109/TEC.2004.827712
- E. Loukarakis, I. Margaris, and P. Moutis, “Frequency control support and participation methods provided by wind generation,” in Proceedings of IEEE Electrical Power & Energy Conference, Montreal, Canada, Oct. 2009.
- E. Muljadi, V. Gevorgian, and M. Singh, “Understanding inertial and frequency response of wind power plants,” in Proceedings of IEEE Symposium on Power Electronics and Machines in Wind Applications, Denver, USA, Jul. 2012.
- R. Sakamoto, T. Senjyu, N. Urasaki, T. Funabashi, and H. Fujita, “Output power leveling of wind turbine generators using pitch angle control for all operating regions in wind farm,” in Proceedings of Intelligent Systems Application to Power Systems, Arlington, USA, Nov. 2005.
- R. de Almeida, E. Castronuovo, and J. Lopes, “Optimum generation control in wind parks when carrying out system operator requests,” IEEE Trans. Power Syst., vol. 21, no. 2, pp. 718-725, May 2006. https://doi.org/10.1109/TPWRS.2005.861996
- A. Žertek, G. Verbič, and M. Pantoš, “Optimised control approach for frequency control contribution of variable speed wind turbines,” IET Renew. Power Gener., vol. 6, no. 1, pp. 17-23, Jan. 2012. https://doi.org/10.1049/iet-rpg.2010.0233
- I. Katic, J. Højstrup, and N. O. Jensen, “A simple model for cluster efficiency,” in Proceedings of European Wind Energy Association Conference and Exhibition, Rome, Italy, Oct. 1986.
- Hydro Québec, “Transmission provider technical requirements for the connection of power plants to the Hydro Québec transmission system.” Feb. 2009.
- P. Boggs and J. Tolle, “Sequential quadratic programming,” Acta Numerica, vol. 4, pp. 1-51, 1996.
- EirGrid, "EirGrid Grid Code Version 5.0", Oct. 2013.
- L.-R. Chang-Chien, C.-M. Hung, and Y.-C. Yin, “Dynamic reserve allocation for system contingency by DFIG wind farms,” IEEE Trans. Power Syst., vol. 23, no. 2, pp. 729-736, May 2008. https://doi.org/10.1109/TPWRS.2008.920071