- Volume 10 Issue 6
DOI QR Code
Application of SFCL on Bus Tie for Parallel Operation of Power Main Transformers in a Fuel Cell Power Systems
- Chai, Hui-Seok ;
- Kang, Byoung-Wook ;
- Kim, Jin-Seok ;
- Kim, Jae-Chul
- Received : 2014.11.24
- Accepted : 2015.09.07
- Published : 2015.11.01
In the power plant using high temperature fuel cells such as Molten Carbonate Fuel Cell(MCFC), and Solid Oxide Fuel Cell(SOFC), the generated electric power per area of power generation facilities is much higher than any other renewable energy sources. - High temperature fuel cell systems are capable of operating at MW rated power output. - It also has a feature that is short for length of the line for connecting the interior of the generation facilities. In normal condition, these points are advantages for voltage drops or power losses. However, in abnormal condition such as fault occurrence in electrical system, the fault currents are increased, because of the small impedance of the short length of power cable. Commonly, to minimize the thermal-mechanical stresses on the stack and increase the systems reliability, we divided the power plant configuration to several banks for parallel operation. However, when a fault occurs in the parallel operation system of power main transformer, the fault currents might exceed the interruption capacity of protective devices. In fact, although the internal voltage level of the fuel cell power plant is the voltage level of distribution systems, we should install the circuit breakers for transmission systems due to fault current. To resolve these problems, the SFCL has been studied as one of the noticeable devices. Therefore, we analyzed the effect of application of the SFCL on bus tie in a fuel cell power plants system using PSCAD/EMTDC.
DG interconnection;Parallel operation;Fuel cell;SFCL, Protection
- K. Y. Kim, S. H. Ji, M. S. Lee, B. M. Kim, D. S. Rho, Y. M. Oh, M. K. Kang, “The Analysis of Operation Characteristic in Large Scale Fuel Cell System”, The Conference on KIEE, pp. 503-504, July, 16-18, 2014.
- M. G. On, M. H. Kim, J. S. Kim, I. K. You, S. H. Lim, and J. C. Kim, “A Study on the Application of SFCL on 22.9 kV Bus Tie for Parallel Operation of Power Main Transformers in a Power Distribution System”, KIEE Trans., Vol. 60, No. 1, Jan., 2011.
- IEEE Std. 1547, “IEEE Standard for Interconnecting Distributed Resources with Electric Power Systems”, 2003.
- Y. H. Chong, H. S. Chai, J. C. Kim, and S. M. Cho, “A Study on the Operation Condition by Electrical Fault in the High Temperature Fuel Cell Plant”, KIIEE Trans., Vol. 27, No. 8, Aug. 2013.
- S. H. Chang, K. H Oh, and J. H. Kim, “Analysis of voltage unbalance in the electric railway system using two-port network model”, KIEE Trans., Vol. 50A, pp. 248-254, May, 2001.
- J. S. Kim, S. H. Lim, and J. F. Moon, et al., “Analysis on the protective coordination on neutral line of main transformer in power distribution substation with superconducting fault current limiter”, KIEE Trans., Vol. 58, pp. 2089-2094, Nov., 2009.
- H. R. Kim, S. W. Yim, and O. B. Hyun et al., “Analysis on recovery characteristics of superconducting fault current limiters”, presented at the Conference on Magnet Technology, Philadelphia, Aug. 27-31, 2007, MT-20.
- J. C. Kim, “Electrical Technology for On-site Practice”, Kidari, 2001.
- Ministry of Knowledge Economy, "Renewable Portfolio Standard Management and Operation Guidelines", March, 2013.
- G. S. Nam, “Hydrogen Fuelcell Handbook”, Sungandang, 2011.
- FuelCell Energy, Inc., "DFC 3000 Specifications"
- R. Venkataraman, and W. Liyingood, "Method and System for Recovering High Power Output Operation of High Temperature Fuel Cells by Using Rapid Load Recovery Procedure", European Patent EP 2 050 161 B1, 2012.
- H. M. Yoon, S. Y. Jung, D. H. Kim, and B. K. Lee, “Dynamic Analysis MCFC for Mass Power Generation System”, Power Electronics Annual Conference, pp. 254-256, 2010.