- Volume 28 Issue 4
DOI QR Code
Study on the Evaluation of the Tension and Contact Resistance of a 3 Φ 3 W Plug-In MCCB
3상 3선식 Plug-In MCCB의 인장력 및 접촉저항 평가에 관한 연구
- Lee, Byung-Seol (Department of Fire Safety Engineering, Jeonju University) ;
- Choi, Chung-Seog (Department of Fire Safety Engineering, Jeonju University)
- Received : 2013.04.12
- Accepted : 2013.07.22
- Published : 2013.08.31
The purpose of this paper is to evaluate the performance of a Plug-In MCCB developed for rapid power supply restoration when the MCCB is installed in a power system and to verify its reliability. Since the developed 3
- H. I. Cho, "Statistics of Electric Power in Korea", KEPCO, 2012.
- Y. S. Park, "Fire Statistics", NEMA, 2011.
- International Electrotechnical Commission, "IEC 60898-1", 2011.
- European Standard, "EN 60898-1", 2011.
- IEC 60050-441, "International Electrotechnical Vocabulary (IEV) Chapter 441: Switch Gear and Control Gear and Fuses", 1984.
- D. W. Kim, K. Y. Lee, H. W. Moon, H. K. Kim and C. S. Choi, "Damage Properties and Overheat Detection Techniques of Connection Parts of MCCB and Terminal Block", Journal of Korean of Institute of Fire Science & Engineering, Vol. 22 No. 4, pp. 54-60, 2008.
- D. W. Kim, K. Y. Lee, H. W. Moon, H. K. Kim and C. S. Choi, "Fire Hazard Analysis of MCCB Terminals in Resistance Load by Connection Failure", Spring Conference of the Korean Institute of Electrical Engineers, pp. 88-90, 2007.
- Korean Standards Association, "KS C 8321, 8111", Korean Agency for Technology and Standards, 2008.
- C. S. Choi, H. W. Kim, K. S. Lee, Y. S. Lim, C. H. Lee and J. H. Chung, "Electrical Fire Engineering", Donghwa Technology Publishing Co., pp. 193-197, 2004.
- C. S. Choi, "Firefighting and Electrical Installation", Donghwa Tech. Publishing Co., pp. 284, 371, 411, 419-423, 2013.
- Korean Standards Association, "K 60898-2 Circuit-breakers for Overcurrent Protection for Household and Similar Installations-Part 2: Circuit-breaker for a.c. and d.c. Operation", Korean Agency for Technology and Standards, 2010.
- Ilsung E&G Com., "Clip Member, MCCB Uuit and Distributing Panel", No.10-0974483, 2010.
- Ilsung E&G Com., "Clip Body, MCCB Unit and Distributing Panel", No.10-1019958, 2011.
- IEC 60943, "Guidance Concerning the Permissible Temperature Rise for Parts of Electrical Equipment, in Particular for Terminals", 2nd edition, 1998.
- Korean Standards Association, "KS C 2127", Korean Agency for Technology and Standards, 2008.